EIHF Isofroid Install his equipment in all mortuary at hospitals. It proposes all the equipment and the materials, necessary for the transport of the deceased (cold boxes), the transfer of bodies (trolley and table), the preservation (refrigirating cells), the mortuary toilet and the embalm care (refrigerating tables or autopsy table).
Racks and Trays
Lifting and Presentation Trolleys
Body refrigerated transport compartment
Wash and drain units
How to equip the technical room?
The death room, referred to in article L. 2223-39 of the general code of territorial communities, must have a public area for families and a technical area reserved for conservation and the preparation of the body, including in the public health institutions, bodies of children that can be reported without the vital life.
The public area:
The public area of the death room includes, at a minimum, a local presentation of the body of the deceased as well as the bodies of the children that can be reported without life, in public health facilities and a local home for families.
It may also include a waiting room for families and a ceremonial hall.
The technical area:
If the room temperature there exceeds 17 ° C, room presentation of the body must be equipped with refrigeration equipment enabling the viewing of the body. This room is provided with a ventilation ensuring a renewal of air of at least a volume per hour during the presentation of the body.
The windows of the local presentation of the body of the deceased as well as body parts of children who could be declared dead, in the public health institutions that give on the outside of the Chamber must be non-transparent glass so the opposite or the public have seen inside the Chamber.
The technical area of the death room includes at least a local of preparing the body and must be equipped, as a minimum, two refrigerated spaces of conservation of the body by incomplete even tranche of 200 deaths each year.
The refrigerated boxes are programmed to operate between temperatures of 0 ° C and + 5 ° C, some can be programmed to operate at temperatures less than or equal to-10 ° C, especially for the conservation of the admitted body on requisition for forensic reasons.
The refrigerated boxes have a self-supporting structure. Signs of the refrigerated boxes must be smooth, rotproof and plurality.
The technical area parts communicate with each other to allow the movement of the body out of sight of the public. For the handling of the bodies used forklifts compatible with refrigerant cells, presentation carts and washing units at the mortuary toilet.
Windows of the technical area parts facing the outside of the Chamber must be non-transparent glass if the opposite or the public have seen inside the Chamber.
The local preparation of the bodies provided for in article 4 of this order is reserved to mortuary toilets, care of preservation of the body mentioned in the 3 ° of article L. 2223-19 of the code of local authorities and, as appropriate, to the levies fine scientist seeking the cause of the deaths as well as withdrawals of prosthetic running through a stack.
Access to the premises of preparation of the body is reserved for the people who perform the operations mentioned in the preceding paragraph.
In any season, the temperature of the preparation room must be at most equal to 17 ° C. The device of ventilation of the premises of preparation of the body has a high input and low output and must ensure a renewal of air of at least four volumes per hour for the duration of the preparation of a body. Forced-air heating systems are prohibited. Rejected outside air is previously treated by a filter, absorbing and deodorant before release.
Wall mounted radiators have no contact with the ground. Electrical installation of the premises of preparation is tight projections.
The ground is without rough edges; its flooring and baseboards must be washed and disinfected intensively without alteration. The walls, ceiling and doors are hard, smooth, rotproof and easily leacher materials.
The arrival of water from the local preparation of the body is equipped with a system separator avoiding any contamination of public drinking water supply network. The room must be equipped with at least a floor drain. The floor drains are equipped with baskets removable and disinfectable. The preparation of the body is equipped with a sink or a pot with water inlet not hands-on, a distributor of paper towels and an emptying.
The furniture is washable and disinfectable base. The table for preparation of the body is 'independent' type.